TOLL FREE 1.800.783.6664
Voice: 813.971.5001 Fax : 813.971.5117
Price starts at
Product Code : FX-1000P2-TC
Manufacturer : Foxcroft
Amperometric Chlorine Residual Analyzer,
220Vac 50 Hz 0-5 Ppm Standard Range, With Second Ki Buffer Pump
Total Chlorine, 3-Digit Display
FX-1000P1-TC measures total chlorine with the second buffer solution feed
pump. It offers several advantages:
Labor can be reduced by pumping the solution and the vinegar from larger
containers. The buffer feed rate using the standard #14 size buffer feed
tubing is 4.3 days per gallon. Pumping from a 5-gallon container allows the
analyzer to run unattended for over 20 days. A customer using the smaller
diameter #13 tubing can extend the solution changeover from every 13 days
for one gallon to 65 days for 5 gallons.
The Foxcroft FX-1000p
Chlorine Residual Analyzer utilizes the most accurate test method to
determine chlorine residual levels in process waters, similar to
that used in lab environment titrator test methods. This makes it an
excellent choice for chlorine control or monitoring applications.
Residual readings are instantaneous and do not rely on "sample and
hold" methods. This minimizes any delay in readings for control
applications. The continuous 4-20 milliamp output signal can be used
to drive chlorine residual control systems and/or chart recorders,
data loggers or SCADA systems. The alarm outputs can alert plant
operators to an out-of-range chlorine residual, or trigger an
autodialer in remote or off-hour situationsThe measuring cell design
incorporates several features to ensure accurate readings, such as;
high-grade gold and copper electrodes, fixed sample and buffer feed
rates, and continuous cell mixing and cleaning. Solid-state analog
electronics provide stable, drift-free, residual readings and output
signal. Electronic isolation eliminates problems from "gound-loop"
and ensures operator safety.
The analyzer is
designed to be relatively maintenance-free, other than adding
vinegar when it runs out. The use of vinegar as a pH buffer is
simple, effective, economical, and environmentally friendly.
Converting the analyzer to read total chlorine, is as simple as
adding Potassium Iodide to the vinegar buffer.
4-20mA Isolated Output,
High and Low Alarms
LED Digital Readout
• Display PPM or Mg/L
Standard Calibration Range
(see chart page 10)
• NEMA 4X Enclosure
Buffer Feed Rate
#14 tubing - (4.5 days
buffer supply use)
Tubing installed, #13
Tubing - (12.5 days
buffer supply use) Buffer bottle wall bracket
• Sample Tubing
1/4” ID x 3/8” OD flexible
3 feet long.
• Discharge Tubing
2 - 5/8” ID x 3/4” OD
flexible PVC tubing
Each piece 3 feet long.
• 110 VAC Power
Wall Mounting Feet
One Instruction Book
• Total or Free
When measuring total chlorine recommend
using option 9 or 10 on page
7 to Feed Potassium Iodide solution.
Commerce Park Professional Center 5309 Technology Dr. Tampa, FL 33647 Ph: 813.971.5001
Fax: 813.971.5117 Email: email@example.com
Copyright © 2014 Omni Controls, Inc. All Rights Reserved. Ecommerce Website Design By - Genesis Web Designs